MEGATEC(8)

NAME
megatec - Driver for Megatec protocol based UPS equipment

NOTE
This man page only documents the hardware-specific features of the megatec driver. For information about the core driver, see nutupsdrv(8).

SUPPORTED HARDWARE

The megatec driver is known to work with various UPSes from Blazer, Energy Sistem, Fenton Technologies, Mustek and many others. The NUT compatibility table lists all the known supported models. Keep in mind, however, that other models not listed there may also be supported but haven't been tested.

On models with both a serial port (RS-232) and an USB port, only the serial port is supported. Connecting a computer which does not have a serial interface to the UPS serial port using a USB-to-serial converter should work, provided the converter is supported by your operating system.

EXTRA ARGUMENTS

This driver supports some extra parameters (see ups.conf(5)):

mfr=string

    Optional. Specify the UPS manufacturer name.

model=string

    Optional. Specify the UPS model name.

serial=string

    Optional. Specify the UPS serial number.

offdelay=int

    Optional. After receiving a shutdown command, the UPS will wait this many minutes before turning off the load. Specify this if the UPS must remain online for a short period of time after the computer has powered down. The default is 0 (turn off immediately).

ondelay=int

    Optional. After turning off the load (see offdelay), the UPS will wait at least this many minutes before coming back online. If line power gets restored before this delay expires, the UPS will wait until it does. If line power gets restored after this delay expires, the UPS will power on the load immediately. The default is 2 minutes.

lowbatt=float

    Optional. Low battery level (%). Overrides the hardware default level. Cannot be used if the driver is unable to calculate the charge percentage for your UPS automatically (see KNOWN PROBLEMS) and the battvolts parameter isn't specified.

battvolts=float:float

    Optional. The battery voltage interval (see KNOWN PROBLEMS).

battvoltmult=num

    Optional. Multiply the reported battery voltage by this number. Some devices report only a fraction of the total battery voltage. The default is 1.

dtr=int

    Optional. Some UPS models need the DTR serial line set to a specific state, either 0 or 1. See also rts.

rts=int

    Optional. Some UPS models need the RTS serial line set to a specific state, either 0 or 1. See also dtr.

ignoreoff

    Optional. This option should be used if upsc(8) shows the UPS status as OFF when it's clearly on. This will force the driver to ignore the OFF status altogether.

sendpace=int

    Optional. This option can be used to change the wait interval between each character that is sent to the UPS, between 1 and 1000 milliseconds. Some models may need this if the default interval (100 milliseconds) proves to be too long, or too short.

UPS COMMANDS

This driver supports some instant commands (see upscmd(8)):

beeper.toggle
    Toggle the UPS beeper. (Not available on some hardware.)

load.on
    Turn on the load immediately.

load.off
    Turn off the load immediately (see KNOWN PROBLEMS).

reset.input.minmax
    Reset minimum and maximum input voltage status.

reset.watchdog
    Restarts the UPS watchdog timeout. The watchdog is started if it isn't running, which means the UPS shuts down one minute after this command is executed for the last time, restarting one minute afterwards. To cancel the watchdog, run the "shutdown.stop" command.

shutdown.return
    Turn off the load and return when power is back. Uses the timers defined by ondelay and offdelay.

shutdown.stayoff
    Turn off the load and remain off (see KNOWN PROBLEMS). Uses the timer defined by offdelay.

shutdown.stop
    Stop a shutdown in progress.

test.battery.start.deep
    Perform a long battery test (Not available on some hardware.)

test.battery.start
    Perform a (10 second) battery test.

test.battery.stop
    Stop a running battery test. (Not available on some hardware.)

KNOWN PROBLEMS

The battery charge (%) value is only a best-effort calculation and may be incorrect, or non-existant, for some UPS models. In any case, you can always resort to finding the voltages at which the battery becomes fully discharged and fully charged, and specify them manually using the "battvolts" option. If you do this, please notify the author of this driver so that information can be added to the NUT hardware compatibility list. Note that if you also specified the "battvoltmult" option, you need to divide the found voltages for fully discharged and fully charged by this number.

Some UPS commands aren't supported by all models. In most cases, the driver will send a message to the system log when the user tries to execute an unsupported command. Unfortunately, some models don't even provide a way for the driver to check for this, so the unsupported commands will silently fail.

Both the "load.off" and "shutdown.stayoff" instant commands are meant to turn the load off indefinitely. However, some UPS models don't allow this. When this is the case, the driver will tell the UPS to turn off the load for 9999 minutes (about 7 days) and a message will be sent to the system log.

Some models report a bogus value for the beeper status (will always be "enabled" or "disabled"). So, the "beeper.toggle" command may appear to have no effect in the status reported by the driver when, in fact, it is working fine.

The temperature value is also known to be bogus in some models.

AUTHOR
Carlos Rodrigues <carlos.efr at mail.telepac.pt>

SEE ALSO

nutupsdrv(8), upsc(8), upscmd(8), upsrw(8)

  Internet resources:
The NUT (Network UPS Tools) home page: http://www.networkupstools.org/