SAFENET(8)

NAME
safenet - Driver for SafeNet compatible UPS equipment

NOTE
This man page only documents the hardware-specific features of the safenet driver. For information about the core driver, see nutupsdrv(8).

SUPPORTED HARDWARE
This driver supports UPS equipment which can be controlled via SafeNet v1.0 for Windows (serial interface only).

EXTRA ARGUMENTS
This driver supports the following optional settings in the ups.conf(5):

manufacturer=value
    Autodetection of this parameter is not possible yet (and it probably never will be). Therefore, this user defined string accepts any name. The default is unknown.

modelname=value
    Like manufacturer above. The default is unknown.

serialnumber=value
    Like manufacturer above. The default is unknown.

ondelay=value
    Time to wait before switching on the UPS (minutes). Defaults to 1 minute.

offdelay=value
    Time to wait before shutting down the UPS (seconds). Defaults to 30 seconds.

UPSCMD
This driver supports some instant commands (see upscmd(8)):

test.battery.start
    Start UPS self test

test.battery.stop
    Cancel UPS self test

test.failure.start
    Start simulated power failure

test.failure.stop
    Cancel simulated power failure

beeper.enable
    Enable the UPS beeper

beeper.mute
    Temporarily mute the UPS beeper

beeper.toggle
    Toggle the UPS beeper

shutdown.return
    Turn off the load and wait for the power to return. Uses the timer defined by offdelay.

shutdown.reboot
    Turn off the load and return. Uses the timers defined by offdelay and ondelay.

KNOWN PROBLEMS
If you run the shutdown.return command with mains present, the output may stay on or switch off and not back on again. The shutdown.reboot command will unconditionally switch on the load again (with or without mains present).

If the driver is called with the '-k' option (or through upsdrvctl shutdown) it tries to detect which command should be used in an attempt to stay off until mains is present again or to cycle the output if the power returned in the mean time. This isn't bullet proof and you should be prepared that the power will either not be shutdown or that it doesn't return when the power comes back.

AUTHOR
Arjen de Korte <adkorte-guest at alioth.debian.org>

SEE ALSO

  The core driver:
nutupsdrv(8)

  Internet resources:
The NUT (Network UPS Tools) home page: http://www.networkupstools.org/